Hardware Factory --------------- Model Number: AP8959EU3 Serial Number: ZA1330021822 Hardware Revision: 02 Manufacture Date: 07/30/2013 MAC Address: 00 C0 B7 B4 66 04 Management Uptime: 1 Day 0 Hours 43 Minutes Network Management Card --------------- Model Number: AP9537 Serial Number: ZA1330022907 Hardware Revision: 05 Manufacture Date: 07/27/2013 Application Module --------------- Name: rpdu2g Version: v5.1.6 Date: Oct 15 2012 Time: 10:34:14 APC OS(AOS) --------------- Name: aos Version: v5.1.9 Date: Oct 15 2012 Time: 09:48:19 APC Boot Monitor --------------- Name: bootmon Version: v1.0.2 Date: Jan 21 2010 Time: 13:35:57Ebay:
Remotely manage outlets so users can turn outlets off that are not in use (prevent overloads) or recycle power to locked-up equipment (minimize costly downtime and avoid travel time to equipment).
Allows users to configure the sequence in which power is turned on or off for each outlet. This helps avoid in-rushes at start-up, which can cause overloaded circuits and dropped loads. Sequencing also allows users to predetermine which piece of equipment is turned on first so other equipment dependant on that unit will function properly.
Full-featured network management interfaces that provide standards-based management via Web, SNMP, and Telnet. Allows users to access, configure, and manage units from remote locations to save valuable time. Associated with this feature is the ability to quickly and easily upgrade the firmware via network download to installed units for future product enhancements.
Define alarm thresholds in order to avoid overloaded circuits. Network and
visual alarms inform the user of possible problems. Local Current Monitoring
Display. The aggregate current draw per power distribution unit is displayed
on the unit via a digital display. The local digital display helps installers
avoid overloaded circuits by providing a visible warning when the current draw
is close to the maximum amperage draw of the strip.
Rack PDU 2G, Switched, ZeroU, 16A, 230V, (21) C13 & (3) C19, IEC309 Cord APC Switched Rack PDU , Input: 200V, 208V, 230V , Input Connections: IEC 309 16A 2P+E , Cord Length: 9.84 feet ( 3 meters ) , Output: 230V , Output Connections: IEC 320 C13,IEC 320 C19 Includes: Installation guide, Locking input power cord, Rack Mounting brackets, Safety guide, Sample locking IEC power cord, Serial configuration cable Output Nominal Output Voltage 230V Maximum Total Current Draw per Phase 16A Output Connections (21) IEC 320 C13 (3) IEC 320 C19 Overload Protection No Input Nominal Input Voltage 200V,208V,230V Input Frequency 50/60 Hz I Input Connections IEC 309 16A 2P+E Cord Length: 3 meters Number of Power Cords: 1 Acceptable Input Voltage: 220-240 VAC Maximum Line Current per phase 16A Maximum Input Current per phase 16A PhysicalNet Weight 5.73 KG Maximum Height 1791.00 mm Maximum Width 56.00 mm Maximum Depth 46.00 mm Shipping Weight 8.59 KG Shipping Height 2002.00 mm Shipping Width 165.00 mm Shipping Depth 114.00 mm Color Black Environmental Operating Environment -5 - 45 ?C Operating Relative Humidity 5 - 95% Operating Elevation 0-3000 meters Storage Temperature -25 - 65 ?C Storage Relative Humidity 5 - 95% Storage Elevation 0-15000 meters Conformance Regulatory Approvals cUL Listed,EN 55022 Class A,EN 55024,EN 61000-3-2,EN 61000-3-3,FCC Part 15 Class A,ICES-003,PSE,UL Listed,VCCI Class A,VDE Standard Warranty 2 years repair or replace Environmental Compliance RoHS,REACH: Contains No SVHCs,Contains Lithium Battery
This is a very similar document that appeaer to have replaced the User Guide above.
However it no longer directly references the 89XX models thta I am working with.
User Guide Configurable Rack Power Distribution Unit Metered-by-Outlet with Switching (990-91135A-001)
Publication Date: October 2018:
Possible programming application: